Click to close
Industry Recents News
|17 Nov 2017||Controlling Efficiency with Zero Touch Provisioning|
|9 Nov 2017||All the Gear No Idea|
|1 Nov 2017||On the Importance of Hiring the Right Specialists in Data Center Management|
|17 Jul 2017||Back to nature|
|16 Jul 2017||Data Center colocation market growing at 14.60% CAGR to 2022: North America accounted for the largest share of the global market|
|11 Jul 2017||The benefits of micro data centers|
|7 Jul 2017||A journal into the hybrid cloud|
|6 Jul 2017||The peculiarities of high-availability Data Center design on a cruise ship|
|3 Jul 2017||Is the public cloud out for disaster recovery?|
On the Importance of Hiring the Right Specialists in Data Center Management
Dateline: 1 Nov 2017
Every other tile in the cold aisle was perforated, leading to inefficient airflow. Cooler air was flowing back into the air handler, creating a delta between warm and cool air of just 68-72°. This was leading to inefficient operation in the air handler and ultimately to the equipment failure. After replacing the tiles, the delta widened to 62- 80°, but it shouldn’t have needed Fogal to spot it. Why wasn’t the data center manager aware?
Back to Top
Copyright 2015 ® Cheval Electronic Enclosure Co., Ltd. All Rights Reserved.